Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||19 December 2016|
|PDF File Size:||2.80 Mb|
|ePub File Size:||2.8 Mb|
|Price:||Free* [*Free Regsitration Required]|
Unhook the top of the DIN rail slot from the rail. Without appropriate precautions, there may be potential difficulties ensuring electromagnetic compatibility in other environments due to conducted as well as radiated disturbance. Do not drill holes above a mounted controller if the protective debris strips have been removed. Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices.
Follow these steps to connect the replaceable battery.
Scripting must be enabled to use this site.
Make sure that the placement of the controller on the DIN rail meets the recommended spacing requirements see Controller Spacing on page 12 for more information. Each product is supplied with markings on the rating o indicating the hazardous location temperature code. Use a power supply that matches the transmitter specifications as shown. Combinations of equipment in your system are subject to investigation by the local Authority Having Jurisdiction at the time of installation.
Be sure that power is removed or the area is nonhazardous before proceeding. For AC-powered controllers, this connection must be made for safety purposes. This could cause an explosion in hazardous location installations. Wiring Your Analog Channels Analog input circuits can monitor voltage signals and convert them to serial digital data as shown in the following illustration. Replace the battery when the controller is powered on.
For more information on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable.
Follow these steps to install your controller on the DIN rail. Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications.
For an additional level of technical phone support for installation, configuration and troubleshooting, we offer TechConnect support programs. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc.
Remove the mounting template from inside the back cover of this document. Make sure your controller is spaced properly see Controller Spacing on page 12 for more information. You can also contact a special Customer Support number for initial help in getting your product up and running. However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters.
IN – Rockwell Automation
Wear an approved grounding wriststrap. Repeat steps 1 and 2 for the second DIN rail latch. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of u0m01, complying with a flame spread rating of 5VA, V2, V1, V0 or equivalent if non-metallic.
Plug the ribbon cable connector into the bus connector. Wiring category 1 2 – on signal ports 2 – on power ports 3 – on communications ports Terminal screw torque 0. Use a static-safe workstation, if available. Follow these guidelines when you handle this equipment: When the battery is low, the indicator is set displayed as a solid um01. Make sure that the MicroLogix system is properly grounded.
While pressing the controller down against the top of the rail, snap the bottom of the controller into position. B mm 7. Drilled fragments that fall into the controller could cause damage. Drill holes through the template. Leave the 1676 debris strip attached until you are finished wiring the controller and any other devices.
United States Contact your distributor. Do not touch circuit components inside the equipment.