IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. 5. Voltages limited by arresters. Arrester power frequency witstand voltage. Resulting . An allowance of at least 5% (IEC ) is recommended. With this.
|Published (Last):||10 September 2009|
|PDF File Size:||3.53 Mb|
|ePub File Size:||13.15 Mb|
|Price:||Free* [*Free Regsitration Required]|
IEC System of Conformity Assessment Schemes
Preview Abstract IEC Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. Contact us svenska Login. Message to your colleague.
When you use our service you can be assured the latest editions and easy access. Selection and application recommendations.
What is a standard? Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to 6099 selecting the type and rating. Sustainable Development Goals and standardisation, how do they connect? Subscribe on standards with our subscription service.
IEC | IEC Webstore
Your shopping cart is empty. SS Valve type surge arresters – Terminology. Fuses and other overcurrent protection devices Substations, surge arresters. It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters. Selection and application recommendations Article no: Related publications IEC Selection and application recommendations Status: Report jec on page.
Subscribe on standards ic Read more.
Read more about SIS Subscriptions. Shopping cart Close cart 0, foreach: TC 37 – Surge arresters rss. This edition constitutes a technical revision. Please note ice the selected standard is invalid. The standard is now in your shopping cart. The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued.
Do you need a multi-user copy? The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition. Valid Buy this standard.
We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. In Annex J, lec aspects ic the old type of SiC gapped arresters are discussed. Surge arresters – Part 5: It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Our prices are in Swiss francs CHF.
This third edition cancels and replaces the second edition published in